To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
I am the
Board member responsible for managing a common heating system for an 18-unit
condo in Boston - 3 units across for six floors and about 36,000 squ ft of
interior space . We currently have a
steam-system using a forced-draft boiler sized for 1,987 MBH gross output and
6,427 sqft steam.
had noise, performance and efficiency concerns regarding this present boiler --
and have received a proposal from a reputable heating contractor to replace the
system with a condensing hot-water system.
There are significant costs to tearing up everyone's to re-pipe for hot
water and a rationale we have been given for taking these costs is a
significant annual savings in fuel.
This hydronic-system proposal sizes for (3) boilers ganged
to provide a combined 1,140 MBH gross output -- about 60% of that of our
current system. I realize that a
condensing boiler operates at a higher efficiency than our forced-draft boiler
-- but the uptick in thermal efficiency from 83% to 96% is only a +15% jump.
been told that the remaining efficiency gain (40% - 15% = 25%) is due to the
operating characteristics of delivering hot-water versus steam heat. I don't find anyone on the Web promoting
such an operational difference between the two types of heat.
seeing a proposal to convert from a grossly over-sized existing boiler -- or
have I missed something in the literature about the special efficiencies of
hot-water over steam heat?
your help on this -- Jim Charnley
0 · ·