To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
I'm work in a building that has a steam boiler with a one pipe pipe steam system. The store in the building has recently been renovated. Another contractor came in and installed a steam to water flat plate heat exchanger. The steam return line from the heat exchanger has an f&t trap and then ties into a wet return. There is banging coming from the return line of the heat exchanger. Some how i have gotten dragged into this. I told the contractor to remove the f&t trap and let it go straight into the wet return. He said the company requires an f&t trap on the return line of their heat exchanger. The company said the same thing when i called, even when i told them it drains into a wet return. Can someone please tell me why you need the f&t trap on the return of the heat exchanger if it ties into a wet return? Thank you.