To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
As many of you know, I've posted my "issues" this week trying to build my control/gauge manifold and already wrecked a Wika 0-20 oz gauge. Today the new 0-3 psi gauge arrived and I finished the job. I cycled the system (two-pipe vapor/vacuum) for about an hour. Low and behold, it looks like it's operating below 4 oz! I shut it down to see how long/how much vacuum would register on the new gauge (by pulling PAST zero of course). Compare with the compound gauge to the left. Can the gauge handle going this far past zero? Any one had a couple years under their belt exercising these expensive little buggers? Would a snubber eliminate the pull from the vacuum or can I install an inline check valve? I'm tired of scampering into the boiler room wringing my hands.
0 · ·