To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
two boiler controld go down at same time?
Hello, I am stumped, got a guy with two Buderus G234 boilers, one with 2107, one without, they are actually not tied together control-wise, a tekmar set point control operates the second boiler. Anyway both of the L8148E controls lost their transformers. I have never seen the transformer go (not that that's a big mystery) but to have both trannys drop at the same time seems puzzling.
I rigged up a 24v trans yesterday and got #1 to fire without blowing my popper fuse I had in line. I wrapped my wire 10 times around the amp claw and came with 1.1 amps during combustion (it was 11.7 amps with 10 wraps)
I replaced the 8148E
I didn't have time to get the second boiler going.
Any ideas what may have caused this? My only guess is a stray voltage surge grabbed the boilers circuit. I did not look at the elec service to see if there were two breakers or just one. I was in a bad hurry.
Wilson Services, Inc