To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Had a goodman air handler with electric heat coils/evap coil go down. Wasn't getting any control voltage out of the transformer----208>24 volts. Had 208 going into the transformer, checked voltage at breakers and all safeties/switches. Replaced with a brand new transformer and same thing, no 24V coming out of transformer but I noticed the transformer got warm to the touch. Talked to the tenant on the way out, and he said he recently installed a wall mount TV near the thermostat. Would a short in the thermostat wire cause the transformer not to give off 24V? There is no neutral hooked up to this unit, just ground. When I go back tomorrow, I'm going to disconnect all thermostat wires and see if I get anywhere. Any other ideas?
0 · ·