To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Drainback design questions
I am doing my best to design a new drainback solar hot water
system to provide domestic hot water and help heat the 1500sq ft concrete radiant floor in my
house in central Virginia. I know that it will not entirely heat our very insulated passive solar house but I am looking to reduce my fire wood consumption. I want to avoid summer overheating so a
drainback system seems like the best choice.
I have room for (8) 4’x8’ AET 32 panels mounted flat on my 5/12 pitch
south facing roof and am looking to install a 120 gal solar storage tank with
an integrated heat exchanger. Sadly I
don’t have room for a larger tank. I am
hoping to set it up to automatically send the excess heat to the radiant floor
during heating months. For safety I
want to make the currently open radiant floor system a closed system which will
add an extra pump and heat exchanger.
For non heating months I will simply turn off the controller that kicks
heat to the floor so that the system will drain back when the tank hits its max
temp. I am attaching an image of how I
see the system and would appreciate any advice.
A few Questions:
1. is 1" copper the correct sizing for feeding 8 panels or should I save a bundle and use 3/4" pipe
2. It looks like most 120 gal tanks have a 20sq ft internal
coil heat exchanger. Is this enough to handle the heat from 256sq foot of
3. should I add a pressure tank and pressurize the drainback
system to reduce the chance of steam if
the system turns on mid-day and runs fluid through 8 super hot panels
4. is the Taco 009 the correct pump for only 9’ of vertical
head? I calculate a total head of 19’
(9' ft vertical head + 50’ of 1” copper pipe + the heat exchanger + a safety of 4’)
5. any advice on sizing the flat plate heat exchanger for
6. I currently have an I link SP-81 pump controller for the
floor pump and would like to pair it with an aquastat that would kick the floor
pumps on when ever the 120 gal tank hits 140* and off when it drops to
130* any recommendations?
Ok that is enough in the question department for now. Thanks for any advice!
0 · ·