To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
We have a customer with a AFG in a 68 willy.Hitting reset like clockwork every 12 -14 days. no evidence of delay or excessive oil in chamber on start up. More than one tech has worked on it and have found the same result Nothing wrong. electrodes replaced, ohms on cad cell good, trans good and even replaced just out of frustration. burner has been pulled and set head amps on motor are good. Pump psi set @ 100 psi and holding on shut down. oil line above ground no visible leaks or damage. ???????