To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Mixing radiant into old cast iron system
Long time reader and occasional poster.
I'd like to put in an entirely new system in an old house. I'd like to keep all the radiators and the excellently fitted old iron pipe while dropping in a new cast-iron boiler and 2 new thin-slab radiant zones.
I have done the heatloss calcs, layed out the pex, pressure tested, fitted slab sensors (tekmar) and laid the dry bed.
Now I'm selecting products to do the controls. I'm set on a traditional Weil-Mclain gold series boiler, but the rest is flexible.
I'd like to come up with a simple combination of controls to handle these 3 zones.
1 Large Cast Iron Radiant Zone
2 Barrier Pex Radiant Slabs
I was considering using set point thermostats in each of the slab zones, a programable thermostat in the main cast-iron zone.
I've built one copper and one steel system in the past, but have never used pex. I'm familiar with Taco and Tekmar controls.
My main concerns are coming up with a sytem with minimal components that can safely reduce the temperature of the cast-iron boiler for the PEX, protect the boiler from cold returns and ensure even supply of water when needed to all 3 zones.
In the past I have used primary/secondary piping but with the PEX i'm not really sure how it's going to look.
Thanks for reading and for your time,
A budding radiant nut,
0 · ·