To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Boiler using too much water
I have a one pipe steam heating system It is a Utica boiler which is less than ten years old. I convented it to gas from oil when I bought the house in March of 2008.
The boiler has an automatic water feed on it. When the boiler runs the auto feed always comes on. If I fill the boiler I can see no leaks in the unit itself. I can't see any obvious steam leaks but the problem is one pipe runs under my dining room which is built on a rock ledge so there is no basement and not even a crawl space. There is a space where the pipe goes in and I can't see in that area.
I have 2 radiators that won't heat and I have replaced the steam valves. One is a 3/4" vent on the top of the radiator and the other is a regular 1/8" valve on the side of the radiator.
I also have a radiator on the second floor that only heats when the heat is on for a long time.
I notices that when the boiler is running the pressure gauge by the boiler does not move. I don't know if the valve is bad or if that is contributing to my problem but I thought I would mention it.
I'm sort of assuming there is a leak in the area that I can't see but if that is the case what should I do?