To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.

# Multiple zone valves

Member Posts: 90
I'm trying to calculate how many zone valves I can put through a 40va transformer.
If I take the zone valve motor amp rating and multiply by 24 volts, divide that total into 40, that's the answer (right)?
Now I'm looking at a honeywell zone valve and it reads the following:
24vac 50 va pilot duty
28.4 amps lock rotor.
Which number do I use?

• Which Honeywell

zone valve are you using. The numbers you posted seem like relay numbers not Honeywell ZV's. If memory serves me Honeywell ZV's use about .2 amps so you can use 5 of them with a 40 VA transformer.

If you are using a NEMA rated class II standard DC20-92 transformer you can exceed rating up to 200%.
• Member Posts: 90
zone valve

If a honeywell ZV drew .2 amps, .2X24=48
Wouldnt I be able to use 8?

• Member Posts: 233
Tim

Would you be so kind as to show me how you calculated that? Or tell me what I'm doing wrong. The .2 amps is a 5th of an amp; 24 volts divided by 5 is almost 5, so each zone valve is drawing 5 va; 40 va divided by 5 va is 8 zone valves. There's probably a de-rating in there somewhere?

Alan
• Member Posts: 16

.2 x 24 = 4.8 not 48

So a 50 VA transformer should be able to handle...

50 / 4.8 = 10.416 rounded to 10 zone valves
• Honeywell in their

literature for their zone valves states 5 ZV,s per 40 VA transformer.

They also have a white paper they put out about 10 years ago that states that a 40 VA transformer can be run at 200% of capacity with only a small drop in voltage. This is how we can run three Taco ZV's with a 40 VA transformer as long as it is NEMA rated standard DC20-92 ClassII.For Taco which draws about 1 amp the math would be 1 x 24 = 24 VA per valve x 3 = 72 VA.

With the Honeywell ZV's at .2 x24 = 4.8 divided into a 50 VA = 10.416666 so I would imagine 8 to 10 would be okay with a 50 VA.

This discussion has been closed.

#### Welcome

It looks like you're new here. If you want to get involved, click one of these buttons!