To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Expansion Tank Pre Charge Pressure
The precharge pressure should be a small amount below the system fill pressure. Some diaphragm tanks will damage the bladder if the bladder is forced against the inlet for long periods. Ideal is for the bladder to be approximately 90% extended in normal operation. If the charge presure is higher than system pressure, then the bladder will be fully inflated and the tank will take on no water until the system pressure rises above the pre-charge pressure. Going in the other direction, if the precharge pressure is lower than the system fill pressure some of the acceptance volume is wasted; could have used a smaller tank.
0 · ·