To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Which circ replaces the old Grundfos UPS 20-42?
But the old 20-42 speed one had a very nice low flow curve (as I read it), perfect for my basement 28ft 3/4" Slantfin run (out of 80ft total basement zone run).
I figure that run is about 5ft of head--20-42 would give 2gpm vs 5gpm by 15-42 or superbrute 15-58. I have an old recently disconnected 20-42 from the family house that I'm thinking of installing at my place just to hold me a few years until I can replace my old boiler. Currently installed is a B&G LR20BF 'Little Rooster' which is way overpumping at 13gpm or so--sounds like an oil well just before it gushes.
Glad that when I do get a new boiler, the new Wilo micro circs will be available.
0 · ·